- 1 What is a fire department connection used for?
- 2 What does FDC on a building mean?
- 3 Why is a Siamese connection used?
- 4 How high can a fire department connection be off the ground?
- 5 What do you pump a FDC at?
- 6 How does a fire riser work?
- 7 Which is the most common type of FDC connection?
- 8 What type of sprinkler system is not required to have a fire department connection?
- 9 What pressure do you pump into a standpipe?
- 10 How does a Siamese valve work?
- 11 How far can an FDC be from a fire hydrant?
- 12 How do Siamese connections work?
- 13 Is a PIV required?
- 14 What are FDC signs?
- 15 What is fire riser?
What is a fire department connection used for?
The Fire Department Connection, also commonly known as the siamese connection, is an important component found on most sprinkler and standpipe systems. When a fire sprinkler system activates, the FDC provides a means for firefighters to connect hose lines to supplement the fire sprinkler system’s domestic water supply.
What does FDC on a building mean?
FDC stands for Fire Department Connection. This is a connection on the exterior of a commercial building where a responding fire department can attach a fire hose and pump water into the building’s stand pipe system supplementing the water pressure to the buidling’s sprinkler system.
Why is a Siamese connection used?
Siamese connections are to be equipped with plugs or caps. This is to prevent dirt and other foreign objects from entering the piping, which would inhibit water flow or prevent the connection from being used during an emergency.
How high can a fire department connection be off the ground?
Fire department connections ( FDC ) shall be located not less than 18 inches and no more than 48 inches above the level of the adjoining ground (NFPA 14 Section 6.4.
What do you pump a FDC at?
All pumpers will pump their capacity at 150 psi at the pump, so increase the throttle slowly until your discharge pressure is at 150 psi while being careful not to run away from your water supply.
How does a fire riser work?
As a fire sprinkler discharges, water flows out of the pipe, or branch line, it’s connected to. When that happens, water moves through the system riser to refill the branch line. These changes in flow and pressure are monitored at the riser by electronic devices called water flow switches.
Which is the most common type of FDC connection?
One of the most common FDCs, known as a Siamese or two-way connection, has two 2 1/2-inch female swivel connections. NFPA requires that all fire department connections use 2 1/2″ National Hose (NH) threaded female couplings unless the authority having jurisdiction designates another specific connection type.
What type of sprinkler system is not required to have a fire department connection?
A fire department connection ( FDC ) is required for most NFPA 13 and 13R automatic sprinkler systems and standpipe systems. They are not required for automatic sprinkler systems protecting one- and two-family dwellings and townhomes.
What pressure do you pump into a standpipe?
The minimum pressure while flowing the required standpipe flow (500 GPM from the hydraulically most remote standpipe and 250 GPM from each additional standpipe, up to a maximum of 1000 GPM for a fully sprinklered building) shall be 100 psi at any valve outlet while flowing 250 GPM through each valve.
How does a Siamese valve work?
Siamese FDCs will contain either a single or double clapper to channel the flow of water coming into the system. If two hoses are connected, the equal pressure will cause the clapper in the middle of the body to let water flow in from each side. Double clappers provide greater control.
How far can an FDC be from a fire hydrant?
I. FDCs shall be no more than 150 feet from a public hydrant. The FDC may be located within 150 feet of a private hydrant if the FDC is connected to the fire sprinkler system by a dedicated pipe that connects on the system side (i.e., downstream) of the sprinkler system check valve.
How do Siamese connections work?
Inspired by the Y-shaped Siamese twins, a Siamese connection is a Y shaped fire department connection with two female inlets through which firefighters can attach two hoses and refill standpipes or sprinkler systems with water. The siamese connection is alternatively called FDC ( Fire Department Connection ).
Is a PIV required?
Up until the 2010 Edition, NFPA 24 required a listed post indicator valve on every connection from a private fire service main to a building unless special criteria were met (NFPA 24 Section 6.3).
What are FDC signs?
Fire Department Connection ( FDC ) signs allow for fire department personnel to easily determine the location of a building’s water supply port in event of a fire.
What is fire riser?
Fire riser is a component of the fire suppression system. It is a pipe connected to a pressurized water source which supplies water to the sprinkler system in the building. It is where the gauges, valves, and alarm devices are located.